We carried out two different projects for LIN.
- The first, a relatively straightforward project in 2016, was for its VIP jet area. A modification to the area’s apron layout meant the ground markings to the parking zones also needed to change. This in turn, due to International Civil Aviation Organisation (ICAO) regulations, meant the area’s lighting needed updating.
- Then in 2018, LIN invited us to upgrade its old lighting system as part of a refurbishment of the entire airport. This upgrade included replacing all the airports inefficient and difficult to maintain High Pressure Sodium (HPS) floodlights – as saving energy was high on LIN’s agenda.
The solution for the first project simply involved installing 4 high masts to house 19 of our Titan 720 Series luminaires. Tried and tested around the world, our Titan Series is perfect for large area lighting projects like this.
The second project was to prove more complex. LIN’s entire lighting system at the time included 262 HPS floodlights that needed upgrading. These floodlights ranged from 400W to 1,000W and were housed on a variety of masts from 9m to 35m.
As part of the upgrade, we also had to deliver 10 Lux across the entire length of the taxiways. This aspect of the project was additionally challenging as ICAO regulations stipulated that the light source, had to come from two directions – to deliver the lighting levels required
To replace the 262 HPS luminaires we used the current masts and housed them with just 175 of our Titan Series floodlights. This was made up of:
- 104 Titan 720 lights.
- 33 Titan 420 lights.
- 28 Titan 320 lights
- And, 10 Titan 160 lights – specifically for the ‘Emporio Armani’ Hanger.
This upgrade cut LIN’s energy use by 53%.
During the planning for this project, the need to hit the apron with light from two sources was built into the overall solution. And it was delivered thanks to our proprietary optics systems.
SEA Aeroporti di Milano, who runs LIN, has asked us to carry out a similar upgrade to another of its airports – the nearby and much larger Milano Malpensa Airport (MXP).
Number of passengers:
Average aircraft movements:
LED floodlights installed:
Lux average values:
LED floodlights installed
BEFORE & AFTER TECHNICAL COMPARISON
|Before||After with LED|
|Number of Projectors||262||277|
|Nominal Power for single appliance||400W / 1000W 16kW||167/326/455/705W|
|Total power absorbed||226.3 kW||105.5kW|
|Energy consumption per year||991426 kWh||462081 kWh|
|Colour rendering index||25||70|
|Average light level||20||25|
want to know more?
All the fields marked with an asterisk (*) are mandatory.